A BIG THANKS goes out to Terry who had the confidence in us to tackle a tough sewer repair.
A home inspection sewer scope revealed a cracked tap connection at the City Main in the street.
We were able to excavate and replace the tap, along with @ 8' of pipe. The rest of the line looks good, it already has a set of 4" outside cleanouts, which is a big upgrade in itself.
This sewer should give many more years of trouble free service.