A BIG THANKS goes out to Jeff for having the confidence in us to repair a problem sewer line.
This duplex rental has been out of service for several days, others have tried to clear it but have failed.
We located the pipe, installed some 4" outside cleanouts, and then we were able to easily clean out the rest of the pipe.
We then scoped the remainder of the pipe to find that the tap is broken at the city connection.
That repair will wait for another day. For now, the tenants are able to use the plumbing like normal.